AMONIAKALNE URZDZENIA CHODNICZE PDF
Chłodnictwo przemysłowe – Urządzenia chłodnicze SABROE – Urządzenia HeatPAC – recip – kompaktowa amoniakalna pompa ciepła ze sprężarką tłokową . najnowocześniejszy olej do kompresorów, w tym amoniakalnych, [. największą polską firmą dostarczającą freonowe urządzenia chłodnicze dla potrzeb przemysłu, klimatyzacji i pomp ciepła (produkujące sprężarki i agregaty chłodnicze, [. Title in Polish, Analiza funkcjonowania instalacji chłodniczej zasilającej lodowiska systemy chłodnicze, czynnik R, amoniakalne urządzenia chłodnicze.
|Published (Last):||1 May 2006|
|PDF File Size:||2.66 Mb|
|ePub File Size:||8.88 Mb|
|Price:||Free* [*Free Regsitration Required]|
You can change the active elements on the page buttons and links by pressing a combination of keys:. Technical progress in the design, application and safety of ammonia refrigeration systems. Assign to other user Search user Invite.
The main idea of the design is desuperheating of hot ammonia stream to prepare water for ice resurfacing.
Facility manages amoniakalbe outdoor ice rinks, two amoniakalhe them serve as recreational ones and other chodhicze speed skating track. Change font size You can adjust the font size by pressing a combination of keys: Get link to the record. Additional information Publication languages: The main requirements for ice rinks applications are shown as well as the possibilities to improve energetic efficiency in similar instalations.
The portal can access those files and use them to remember the user’s data, such as their chosen settings screen view, interface language, etc.
Assign yourself or invite other xhodnicze as author. Than heat recovery potential is taken into account and consequently the design of heat recovery system is presented.
Bonca, Zenon (1951- ).
Assignment does not change access privileges xhodnicze resource content. It considers maximum heat gains that could occur and as well as in standard conditions basing on weather data for every hour of the year.
For that the minimal lenght of heat exchanger in water tank was determined. Refrigerating system consists of ammonia chiller which is cooling the secondary refrigerating circuit filled with glycol solution. It allow to create list of users contirbution.
Basing on electric energy usage data, maximal electric power demand and total seasonal energy consumption for refrigeration was estimated. This values are compared to funds for investments determined by the investor.
Operating time is from November to beginnig of March. Application of amonia brine cooling systems. You can change the cookie settings in your browser. Assign Wrong email address.
By using the Infona portal the user accepts automatic saving and using ammoniakalne information for portal operation purposes. Finally the energy and cost savings are calculated as well as amoniakalnee SPBT factor. Also the proposition to modify contract with electric energy distributor was made.
Fields of science No field of science has been suggested yet. Thesis evaluates the refrigerating system in reference to avalible technologies, legal aspects and environmental impact.
High contrast On Off. You’re going to remove this assignment.
Sprężarkowe amoniakalne instalacje chłodnicze – Wytyczne wykonania montażu – Google Books
Submitting the report failed. If the error persists, contact the administrator by writing to support infona.
You have to log in to notify your friend by e-mail Login or register account.